Tricks Of The Trade: Tackling Sewage Odors
Lenny Allen Director of Maintenance Ruidoso Municipal Schools Ruidoso, NMAThanks for writing, Lenny! It sounds as if you understand the basic engineering of sewer systems so I’ll avoid discussing that further. I have encountered this type of issue and it is a dreaded one! There are three more issues that you did not mention and that I have personally encountered in my career.
- If vent stacks are too short and/or too close to rooftop HVAC units (RTU) this can be a problem. Newer RTUs have adjustable fresh air vents to provide a proper fresh air mixture; these can suck in methane emissions from the vent stack if it’s too close and/or not high enough to get proper draft to take it away from the building.
- Cracked pipes in the wall are another possibility. The most cost-effective way to begin testing for this is with a plumbers smoke. The pipes are filled with a special smoke so you can visually see where the methane gas is going, or not going.
- Bad seals in the water closets and urinals. There are no P-traps behind or below water closets or urinals. If the seal is old, dried out, or shifted, you have a straight shot into the methane gas supply.
Other posts by